sop for Action Plan In Case Of Electrical Power Failure
To lay down a procedure to describe the Action plan in case of electrical power failure other than normal power change over time.
This Standard Operating Procedure is applicable for procedure involved in the Action Plan in case of Electricity power failure other than normal power change over time 3-5 Minutes, to be followed at formulation plants
3.1 Officer / Executive Engineering shall be responsible for the execution of this procedure.
3.2 Engineering Manager shall be responsible for the implementation of this SOP.
3.3 Head QA/designee shall be responsible for the compliance of this SOP.
4.0 Abbreviations and Definitions
SOP : Standard Operating Procedure
No : Number
QA : Quality assurance
Qty : Quantity
HVAC : Heating ventilated air condition
5.1.1 Normal Power Change Over duration from DG Set to UPCL within 1 – 2 Minutes.
5.1.2 Normal Power Change Over duration from UPCL to DG Set within 3 – 5 Minutes
5.1.3 The power failure time exceeds from 5 minutes, it shall be considered as power failure. The above time limit is based on normal power change over.
5.2.1 Immediately inform to Head of Engineering, Head of QA, Head of QC and Head of Production regarding the Electrical power failure.
5.2.2 A separate SOP followed by production department for Action Plan in case of electrical power failure.
5.2.3 After proper communication to all concerns identify the fault and get it repaired.
5.2.4 Again inform to all concerns before Putting power supply ON Put ON the power supply where is required.
5.2.5 Start all the necessary utilities as per their start up procedure.
5.2.6 Start the HVAC System as per requirement of users
5.2.7 Start the Purified water system as per the start up procedure after system failure
5.2.8 Ensure all machines and system for proper functioning.
5.2.9 Record of power change over is maintained as per SOP of Diesel Generator.
6.1 Master copy – Documentation Cell (Quality Assurance)
6.2 Controlled copies – Engineering Department