sop for water cooled chiller operation
1.1 To lay down the procedure of cooling chillers.
2.1 This procedure is applicable for 120 TR chillers
3.1 QC Officer or QC Executive
4.1 QC Manager
5.1 Let us make sure that inlet and outlet valves of condenser cooling water pump primary and secondary chilled water pumps are open
5.2 Ensure that inlet and outlet valves are ok and chiller pipeline condenser and evaporator are open
5.3 Let us make sure that sufficient water is available in balancing tank and cooling tower.
5.4 If all are ok press the green button chilled water pump cooling fan and of condenser cooling water
5.5 Let us make sure that evaporator and condenser water pressure Limit (1 to 3 Kg/Cm2 ) and secondary water pressure limit (1.5 to 3.5 Kg /Cm2 ) then start the chiller
|Sr. No.||Abbreviation||Extended Form|
|2.0||SOP||Standard Operating Procedure|
|3.0||TR||Ton of Refrigeration|