sop for Replacement of UV light of purified water plant
To lay down a procedure of replacement of UV light .
This Standard Operating Procedure is applicable for replacement of UV light to be followed at formulation plants
3.1 Engineering Officer / Executive shall be responsible for the execution of this procedure.
3.2 Engineering Manager shall be responsible for the implementation of this SOP.
3.3 Head QA/designee shall be responsible for the compliance of this SOP.
4.0 Abbreviations and Definitions
SOP : Standard Operating Procedure
QA : Quality assurance
PW : Purified Water
ER : Engineering
UV : Ultra vailot
5.1 The UV light shall be regularly monitored for its proper function on daily basis by the
5.2 Any failure observed in the functioning of the UV light may leads to the shutdown of the
purified water plant .
5.3 The UV light shall be replaced at an interval of every 06 month or upon completion of
7000 burring hours whichever is earlier .
5.4 In case if the UV light needs to be replaced due to in proper functioning .the same
replaced as and when required or depending upon QC & micro analysis report of the
purified water .
5.5 The replacement or maintenance work performed if any in the UV light shall be
Recorded in the format
6.0 Forms and Records
6.1 UV Replacement Record Purified Water Plant – Annexure-1
7.1 Master copy – Documentation Cell (Quality Assurance)
7.2 Controlled copies – Engineering Department.